First of all, download the user manual for your system, this gives you all the information about how your system operates.
Yes, as long as the fitter has connected the central control unit to the air conditioning or heating unit. If so, the air conditioning unit can be started up from any Zoning thermostat as long as there is a temperature demand and the Master thermostat is not in MASTER OFF.
Use a suitable communication gateway or interface for the climate-control units. Check the compatibility lists in the support section. If there is no interface, also see the support section for conventional connection diagrams. Do not hesitate to contact us for any other types of connection.
This is not recommended. At a technical level, the system becomes more inefficient, inverter modulation is not optimal, ventilation speeds are not modulated in accordance with the zones in demand, and the user is forced to change mode in the zoning system and also in the machine’s thermostat. If you have an old machine or there is no gateway with the machine currently installed, you can use the zoning system without any problems, although in energy terms it is not as efficient as using an interface. Check the support section for the connection diagrams.
The Master thermostat is another zone thermostat but with 3 extra features compared to the others: it allows the WHOLE system to be switched off, it makes it possible to perform weekly programming of the entire system and, finally, it is the thermostat that imposes Cold /Hot mode on the unit. See the user manual, you will find all the information there.
In the classic Zoning systems it is mandatory since the unit requires this to start up the system. With the new Zity control system the mode and start-up can be imposed from any remote system (BMS, WIFI, etc.) and it is not mandatory to fit the Master thermostat as long as there is another auxiliary system.
Contact the fitter who did the installation, they will probably be able to help you. If you don’t know anyone, email us to ask for help email@example.com
First of all, the fitter should give you a warranty sheet on the day when the system installation is completed. If you don’t have it, find the sales invoice.